Hours - Monday & Tuesday 10AM - 2PM
IMPORTANT INFORMATION ABOUT YOUR DRINKING WATER Total
Trihalomethanes (TTHM) MCL Violation at Cibola Mutual Water Company
Our water system recently violated a drinking water standard. Although this incident was not an emergency,
as our customers, you have a right to know what'happened and what we did (are doingl to correct this
We routinely monitor for the presence of drinking water contaminants. Testing results from January 2Ot9-
Oct. 2019 show that our system exceeds the standard, or maximum contaminant level (MCL), forTTHM. The
standard for TTHM is 0.080 mg/1. lt is determined by averaging allthe samples collected at each sampling
location for the past 12 months. The level of TTHM averaged at two of our system's locations for January
2Ot9- Oct. 2019 was 0.085 mg/L for one and 0.092 mg/L for the other.
What should ldo?
o There is nothing you need to do. You do not need to boil your water or take other corrective actions.
lf a situation arises where the water is no longer safe to drink, you will be notified within 24 hours.
o lf you have a severely compromised immune system, have an infant, are pregnant, or are elderly,
you may be at increased risk and should seek advice from your health care providers about drinking
What does this mean?
This is not an emergency. lf it had been an emergency, you would have been notified within 24 hours.
TTHM are four volatile organic chemicals which form when disinfectants react with natural organic matter
in the water.
People who drink water containing trihalomethanes in excess of the MCL over many years may experience
problems with their liver, kidneys, or central nervous system, and may have an increased risk of getting
What is being done?
We have lowered the amount of water in the storage tank to two days of storage, so water is fresher when
entering the distribution system. Applying for a grant to install equipment to lower TTHM's. We anticipate
resolving the problem within the next 12 months.
For more information, please contact Kathi Frice at928-857-3506 or 5948 Levee Rd. Cibola, M.85328.
*Please share this information with all the other people who drink this water, especially those who may
not have received this notice directly (for example, people in apartments, nursing homes, schools, and
businesses). You can do this by posting this notice in a public place or distributing copies by hand or mail. *
This notice is being sent to you by Cibola Mutual Water Company. State Water System lD#: AZ04-LSL23.
Date distributed: 11/06/2019